iPRD-DC 40r 1000PV modular surge arrester - 2P - 1000VDC with remote transferShow more characteristics >
Main range of productActi 9 product nameActi 9 iPRD-DC device short nameIPRD-DC product or component typeSurge arrester with pluggable cartridge poles description2P output typeContact (volt-free) signal contacts composition1 SD (1 C/O) surge arrester typeElectrical distribution network Complementary surge arrester class typeType 2 surge arrester technologyMOV [Ue] rated operational voltage1000 V (+/- 10 %) DC [In] nominal discharge current15 kA [Imax] maximum discharge current40 kA [Ucpv] maximum continuous operating voltageDifferential mode : 1000 V L+/L-Common mode : 1000 V L+/PECommon mode : 1000 V L-/PE [Up] voltage protection level<= 3.9 kV type 2 common mode L+/PE<= 3.9 kV type 2 common mode L-/PE<= 3.9 kV type 2 differential mode L+/L- disconnector device typeIntegrated disconnector local signallingFlag color: white/red signalling circuit voltageAC : 250 V 50/60 Hz signalling output current0.25 A mounting modeClip-on mounting supportDIN rail 9 mm pitches6 height81 mm width54 mm depth69 mm product weight400 g colourWhite ( RAL 9003 ) response time<= 25 ns connections - terminalsTunnel type terminal 2.5...16 mm² flexibleTunnel type terminal 2.5...16 mm² flexible with ferruleTunnel type terminal 2.5...25 mm² rigid wire stripping length14 mm tightening torque3.5 N.m Environment standardsUTE C 61740-51EN 50539-11 product certificationsCE IP degree of protectionOn front face : IP40On terminal : IP20 IK degree of protectionIK03 relative humidity5...90 % operating altitude2000 m ambient air temperature for operation-25...60 °C ambient air temperature for storage-40...85 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CADSizeAdd to My DocumentsInstruction sheetSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.