circuit breaker Compact NSX250H - 250 A - 3 poles - without trip unitShow more characteristics >
Main rangeCompact range of productNSX100...250 product or component typeBasic frame device short nameCompact NSX250H device applicationDistribution circuit breaker nameCompact NSX250H poles description3P [In] rated current250 A ( 40 °C ) [Ui] rated insulation voltage800 V AC 50/60 Hz conforming to IEC 60947-2 [Uimp] rated impulse withstand voltage8 kV conforming to IEC 60947-2 [Ue] rated operational voltageAC 50/60 Hz conforming to IEC 60947-2 breaking capacity codeH breaking capacity50 kA Icu at 500 V AC 50/60 Hz conforming to IEC 60947-210 kA Icu at 660/690 V AC 50/60 Hz conforming to IEC 60947-235 kA Icu at 525 V AC 50/60 Hz conforming to IEC 60947-265 kA Icu at 440 V AC 50/60 Hz conforming to IEC 60947-270 kA Icu at 380/415 V AC 50/60 Hz conforming to IEC 60947-2100 kA Icu at 220/240 V AC 50/60 Hz conforming to IEC 60947-215 kA at 600 V AC 50/60 Hz conforming to UL 50865 kA at 480 V AC 50/60 Hz conforming to UL 50885 kA at 240 V AC 50/60 Hz conforming to UL 508 suitability for isolationYes conforming to EN 60947-2Yes conforming to IEC 60947-2 pollution degree3 conforming to IEC 60947-1 Complementary control typeToggle mounting modeFixed protection typeWithout protection mechanical durability20000 cycles conforming to IEC 60947-2 electrical durability10000 cycles 440 V AC 50/60 Hz In conforming to IEC 60947-210000 cycles 690 V AC 50/60 Hz In/2 conforming to IEC 60947-220000 cycles 440 V AC 50/60 Hz In/2 conforming to IEC 60947-25000 cycles 690 V AC 50/60 Hz In conforming to IEC 60947-2 Environment IP degree of protectionIP40 conforming to IEC 60529 IK degree of protectionIK07 conforming to IEC 62262 Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsAvailable Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CADSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.